IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||25 April 2012|
|PDF File Size:||16.33 Mb|
|ePub File Size:||3.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
The procedures are based on theoretical studies, test results, and experience. IEC Surge arresters – Part 1: Protective equipment is defined as the main circuit apparatus and ancillary equipment, which are part of a series capacitor installation, but which are external to the capacitor part itself.
Your basket is empty. It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment.
IEEE IEEE Standard for Series Capacitors in Power Systems Capacitors and assemblies of capacitors, insulation means, switching, 600999-5 equipment, and control accessories that form a complete bank for inserting in series with a transmission line are applied. They are not used in general to provide surge protection. Click to learn more.
This third edition cancels and replaces the second edition published in The way these transmission-line choices will improve or degrade lightning 600999-5 is also provided. Low-voltage limiters are covered under Clause 7. Where technical information is not readily available, guidance is provided to aid toward proper surge protection and to reduce interference to communication, control, and protection circuits due to surges and other overvoltages.
Surge ieec components, current at the date of this publication. It applies to non-linear resistor type gapped surge arresters as defined in IEC and to gapless metal-oxide surge arresters as defined in IEC Our prices are in Swiss francs CHF.
The faster, easier way to work with standards. Non-linear resistor type gapped surge arresters for a. Worldwide Standards We can source any standard from anywhere in the world.
It also gives the lists of the standard withstand voltages from which the rated withstand voltages should be selected. Definitions, principles and rules This part of IEC applies to 6009-95 a.
BS EN 60099-5:2013
The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued. What is a standard?
Electrical protection equipment, Three-phase current, Withstand voltage, Surge 600099-5, Rated voltage, Coordination, Electrical insulation, Lightning protection, Overvoltage protection, Surge limiters, Selection. You may find similar items within these categories by selecting from the choices below:.
Included are requirements for safety, rating, and protective device levels. Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. This standard defines the terms used; defines the quantities to be measured; describes test and measuring circuits which may be used; defines analogue and digital measuring methods required for common applications; specifies methods for calibration and requirements of instruments used for calibration; gives guidance on test procedures; gives some assistance concerning the discrimination of partial discharges from external interference.
Complex applications of surge protection practices may require specialized study by experienced engineers. Ied surge arresters with external series gap EGLA for overhead transmission and distribution lines of a. Shopping cart Close cart 0, foreach: Though it will be many years before the both standards are virtually the same, this is a first step.
Protective equipment for series capacitor banks This part of IEC covers protective equipment for series capacitor banks, with a size larger than 10 Mvar per phase. Message to your colleague.
BS EN – Surge arresters. Selection and application recommendations
Report error on page. Subscribe on standards with our subscription service. They may be associated with other devices such as contactors for self-restoring arrangements. Artificial pollution testing of surge arresters This standard gives the basic principles of artificial pollution testing of non-linear resistor type valve type surge arresters.
Computational guide to insulation co-ordination and modeling of electrical networks This technical report gives guidance on conducting insulation co-ordination studies which propose internationally recognized recommendations for the numerical modeling of electrical systems including arresters and for the implementation of deterministic and probabilistic methods adapted to the use of numerical programs.
Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification. What makes this amendment so unique is that it is virtually identical to the test procedure published in IEC in While some parameters such as voltage, routing, and capacity may be predetermined, other decisions are made at the discretion of the designer. Its object is to give information in terms of methods, modeling and examples, allowing for the application of the approaches presented in IECand for the selection of insulation levels of equipment or installations, as defined in IEC Surge arresters – Part 5: Valid Buy this standard.
This standard recommends that the selected withstand voltages should be associated with the highest voltage for equipment.